On 01/25/2013 03:46 PM, stan_katz wrote:
Going from what I had on 465Bs the triggering problem is often that
the tunnel diodes have changed in value.
There are many! threads about this in the archives.
It may be worth your time to try swapping the TDs from the B sweep section
with the A section to see if things change.
I had this problem come up when I was hunting for a process control network
problem while working in factory in a different country.
I swapped the TDs and the scope has been near perfect ever since.